By RT Wood; Oak Ridge National Laboratory. .; United States. Dept. of Energy.; United States. Dept. of Energy. Office of Scientific and Technical Information
Read or Download Advanced Reactor Licensing : Experience with Digital I&C Technology in Evolutionary Plants PDF
Best technology books
This eight-volume set offers cutting-edge info on infrared and electro-optical structures. The guide has been revised, and contours forty five chapters written by means of eighty specialists in IR/EO expertise. topics addressed comprise passive EO structures and atmospheric propagation of radiation.
Know-how options for Behavioral EducationMary Gregerson, editorEvolving along technological advances is a brand new iteration of tech-savvy, media-attuned scholars, quite in graduate and clinical courses. yet whereas a lot is being made from a turning out to be electronic divide among academics and inexperienced persons, creative teachers are utilizing the recent digital media to layout academic ideas which are inventive and functional, attractive and potent.
Dieser Technische Lehrgang erklärt Theorie und Funktionsprinzip des Stoßdämpfers. Er zeigt die praktische Anwendung und erklärt die verschiedenen Bauarten. Beschreibungen zu Stoßdämpfertest und Fehlererkennung komplettieren die Darstellung.
- High Performance CMOS Range Imaging: Device Technology and Systems Considerations (Devices, Circuits, and Systems)
- Drehimpulse in der Quantenmechanik (Teubner Studienbücher Physik) (German Edition)
- The Boundary Element Method with Programming: For Engineers and Scientists
- Between Reason and Experience: Essays in Technology and Modernity (Inside Technology)
- Drinking Water Treatment: Focusing on Appropriate Technology and Sustainability (Strategies for Sustainability)
Extra info for Advanced Reactor Licensing : Experience with Digital I&C Technology in Evolutionary Plants
This ensures the integrity of the transfer process from the mainframe computer to the microcomputer. The checksum calculation is repeated throughout the microcomputer operation. The change control and configuration management for the hardware follows corporate drafting standards used for previous generation protection systems. After installation, the executable code that has been burned into programmable read-only memory (PROM) was treated as hardware. The microprocessor printed circuit board is imprinted with a drawing number that defines, among other things, the software configuration.
6 Software Errors United Kingdom Commissioning testing of HICS at the Sizewell B Nuclear Power Station revealed an error in the system software. The software error, which was in the'data network controller, was easy to uncover and reproduce. Under burdened operation, the data buffer management could corrupt the data. The problem occurred at a threshold, so it was easily detected after the threshold was reached. However, the software error was a subtle problem with dynamic data buffers that is not amenable to analysis using formal methods.
For SDS1, the trip computer design requirements and design description consisted of an English overview description and a corresponding mathematical functional description based on a box-structured method. The design description described the 25 interface requirements between hardware and software components. The required software functions contained in the design requirements and design were combined to form the "virtual" trip computer software requirement specifications. For SDS2, the software requirement specifications were written using function tables.